UL Warns of Potentially Hazardous Receptacle
NORTHBROOK, Ill, April 30, 2013 /PRNewswire/ -- The following is a notification from UL to consumers, electrical installers and Authorities Having Jurisdiction (AHJs) that the duplex receptacle identified below may pose a fire or shock hazard. The receptacle does not comply with UL's safety requirements and is not authorized to bear the UL Mark. The receptacle is employed in lighting controllers sold for use in greenhouses, indoor gardening and hydroponics applications. The receptacles may also have been sold individually.
Name of Product: Duplex Receptacle referred to as a Universal X-Plug 120-240V Receptacle.
Number of Units: 2000.
Manufacturer: Zhejiang Trimone Co., China.
Date of Manufacture: 2012.
Hazard: The receptacle can accept plugs for either 120 or 240 volt products. A potential fire or shock hazard exists if the receptacle is not wired to match the voltage rating of the device plugged into the receptacle.
Identification: The receptacle is a duplex outlet with both slots having a "T"-shaped opening. The receptacle can accept 120 and 240 volt, 15 and 20 amp plug types. It can also accept a polarized type two prong plug, in either orientation. The receptacle may have "E243553" stamped into the metal mounting tab.
On the product: The product bears an unauthorized UL Mark.
Sold at: The receptacles are known to be sold by Titan Controls as part of a lighting controller at www.Titancontrols.net. They may have been sold by other retailers.
Photos of the product can be found at www.ul.com/newsroom.
UL is a premier global independent safety science company with more than 118 years of history. Employing more than 10,000 professionals with customers in over 100 countries, UL has five distinct business units – Product Safety, Environment, Life & Health, Knowledge Services, and Verification Services – to meet the expanding needs of our customers and to deliver on our public safety mission. For more information on UL's family of companies and network of 95 laboratory, testing, and certification facilities, go to UL.com.
Media Relations Manager, UL
T: +1 847-664-1966
More by this Source
UL warns of counterfeit UL Mark on USB power adapter
Nov 27, 2013, 09:00 ET
UL Warns of Counterfeit UL Mark on Containers of Fire Foam Liquid Concentrate
Nov 27, 2013, 09:00 ET
Browse our custom packages or build your own to meet your unique communications needs.
Learn about PR Newswire services
Request more information about PR Newswire products and services or call us at (888) 776-0942.